Innovations in Comfort, Efficiency, and Safety Solutions.
S4 Open Appliance Product Enhancements
BBMD, Multistate Objects, & Smart Data Points
The S4 Group, Inc
When it comes to
improving our S4 Open products, partner feedback is always at the heart
of our development efforts. The next release will include support for BBMD as well as a new concept that we are
calling Smart Data Points. BBMD is the standard BACnet service
that allows IP broadcast based discovery transactions to span IP
subnets. In most cases, the S4 Open BACnet-N2 Router is installed with
a traditional global controller from the BAS manufacturer. It was not
historically necessary for the BACnet-N2 Router to support
this service. With the BAS industry evolving towards private and public
cloud based services the BBMD enhancement was added to the appliance
for a specific project. The customer needed to pull data into a cloud
based energy management system. This is the first example of our
Open Appliances used as an on-site agent for a cloud based service in
addition to being used as a gateway to on premises BACnet applications
and services. We are preparing for the field testing of this
service within the next few weeks.
The original implementation of the BACnet stack for the BACnet-N2 Router did not include support for Multistate BACnet objects, MSI, MSO, and MSV data types. Instead, the BACnet-N2 Router published that data as analog objects, and it deferred to the BACnet client or application to interpret the data. That support is in the release about to enter field-testing. Included is the ability to specify the enumerations associated with these data types. Similarly, we did not originally include the ability to provide enumerations for binary data objects BI, BO, and BV. That capability is in this release.
Analog data objects, AI, AO, and AV did not originally include the ability to specify the Engineering Units associated with these points. In this release, the Device Type Templates for all N2 devices and applications define the configured Engineering Units, the S4 Open Management Console provides the ability to edit these assignments, and the BACnet protocol enhanced to publish the information as point attributes.
One of the reasons for not previously including support for BACnet
Multistate data objects was that the numeric value of many Metasys
points did not cleanly map to BACnet Multistate objects. There needed
to be a way to define, and maintain, the required data transformations.
The concept of Smart Data Points, along with the introduction of
virtual points addresses this need in the upcoming release of the
Virtual points are a new feature of emulated BACnet devices. They do not have a physical presence on the N2 bus. They can be of any data type and are independent of the published protocol. The domain of a virtual point is the device where it is defined. Operations are confined to the emulated device itself, that is, references to real N2 points are restricted to the instance of points in the device containing the Smart Data Point. Virtual points are containers for performing calculations and data transformations. They can be published to BACnet just as we publish N2 points to BACnet. Each is assigned a unique BACnet instance number and all appropriate BACnet properties for its object type.
Combine virtual points with JCBasic compatible scripts and the result is Smart Data Points. The scripts driving the data are triggered by reading or writing to the point. An example would be a MetasysŪ Multistate variable that has values 0, 1, 2, and 3. A script would shift these values by 1 to bring them in compliance with the valid data range for BACnet MSV data objects (positive integers) on read and write operations to the virtual point. Read operations would reference the underlying N2 point and make the appropriate adjustments. Write operations would make the adjustment then write through to the underlying N2 point.
The S4 Open Appliances feature a Configure Wizard that automatically
discovers all N2 devices on the bus, determines the hardware type, and
the application loaded in the hardware, assigns the point mapping and
publishes to BACnet. Device Type Templates are the S4 Open Appliance
technology that provides the point mapping model for each Hardware
platform / application combination. Therefore, if a Smart Data Point is
defined in a device type template each assignment of that template to a
N2 device creates a new instance of the virtual point and its
The next logical step is to include multiple Smart Data Points in one
device type template. The result is a Smart Device that can be used to
transform the operation of legacy N2 devices into BACnet-compliant
devices using all the standard BACnet data objects. Take this concept
just a little bit farther and a Smart Device hosted by the BACnet-N2
Router can theoretically make a legacy Metasys VAV controller emulate
the current generation BACnet compliant VAV controller of another
manufacturer. The BACnet-N2 Router cannot change the application
specific logic within a N2 device. But, it does have complete
control over what is published to BACnet. Think of the possibilities!
[Click Banner To Learn More]
[Home Page] [The Automator] [About] [Subscribe ] [Contact Us]